Am using a 13 year old Onan running on propane to power a work trailer. Recently the florescent lights have started going off after about an hour and then come back on in about 20 mins. Changed ballasts on both lights and bulbs. Both lights are on the same switch. Voltage is good 120. The frequency is high. Question is would the high frequency cause the ballast to over heat and shut down?